Major energy savings thanks to Free Cooling
Direct Free Cooling enables energy savings of up to 80 %.
|Operating mode||Outside temperature||Operation|
|Free Cooling||Outside temperature between supply air temperature set point and minimum frost protection temperature||Outside air damper opens. Outside air flows through the filter directly into the unit, then into the Data Center; compressor off. The circulating air and outside air dampers are open if the outside temperature drops or the heat load decreases. They mix circulating air with the outside air, keeping the supply air temperature constant; compressor off.|
|Adiabatic Free Cooling||Outside temperature above supply air temperature set point||If the outside temperature exceeds the supply air temperature set point, an adiabatic cooling unit cools the outside air, exploiting the available Free Cooling potential to the full. Outside air damper open; compressor off.|
|Mixed mode||Outside temperature rises continuously||Compressor is switched in for support to exploit Free Cooling mode to the full, outside air damper open, compressor running in partial load mode.|
|DX mode||Outside air outside the range for Free Cooling or Mixed mode||The unit runs in Compressor mode; outside air damper closed.|
|Mechanical cooling||Free Cooling||Adiabatic cooling, humidification||Condenser module for DX|
|DX coils||Direct Free Cooling||Direct Adiabatic Cooling||Condenser module for DX|
|DX coils||Direct Adiabatic Cooling (air)|
Indirect Free Cooling (water)
|Direct Adiabatic Cooling||Exhaust air module for Direct Free Cooling|
|No mechanical cooling||No Free Cooling||Steam humidifier||Liquid cooler for CW|
- Call us toll free at
Technical support is available 24/7/365.